Accepta 4322 is a high performance; high molecular weight anionic latex polyacrylate based flocculant with a 20% mole charge.
Accepta 4322 is used as a flocculant for clarification, filtration and effluent systems and other processes.
Accepta 4322 is recommended for use in non-potable raw water clarification, primary and secondary effluent clarification, filtration and clarification of brine in Chlor-Soda plants where the polymer must be N free.
- High performance anionic high molecular weight latex polyacrylate
- Excellent when used as a flocculant for effluent systems and other processes
- Ideal for non-potable raw water clarification, primary and secondary effluent clarification, filtration and clarification of brine in Chlor-Soda plants
|pH:||7.0 ± 1.0 @ 5 g/1|
|Approx. bulk density:||1.05|
|Viscosity (cps):||1200 water|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
Accepta 4322 is best applied as a 0.01 - 0.05% solution.
NOTE - Do not exceed 1.0% strength otherwise viscosity rises rapidly.
The dosage details provided for Accepta 4322 are typical and can be refined by on site testing.
As a primary flocculant for settling use 1 to 5ppm.
For in line filtration use 1 to 5ppm.
For sewage treatment use 1 to 30ppm.
For oily waste water clarification use 1 to 10ppm.
It is always advisable to carry out a 'Control Of Substances Hazardous to Health' (COSHH) assessment before use.
For further technical assistance please contact Accepta.
Safety, Storage & Handling
For full details concerning safety precautions, storage and handling procedures for Accepta 4322 please refer to the latest Safety Data Sheet. To download the latest safety data for this product use the following link: