Accepta 2624 is a high performance wide spectrum biocide developed for the treatment and protection of cooling water systems.
Accepta 2624 is an efficient wide-spectrum anti-microbial that is effective across a broad pH range.
Accepta 2624 inhibits planktonic organisms and also exhibits biofilm removal properties.
Accepta 2624 is non-ionic and non-foaming and is compatible with halogens, corrosion and scale inhibitors normally encountered in water treatment.
- High performance wide spectrum biocide
- Wide-spectrum anti-microbial
- Effective across a broad pH range
- Non-ionic and non-foaming
- Fully compatible with halogens, corrosion and scale inhibitors normally encountered in water treatment
- Convenient liquid product
|Colour:||Clear, pale yellow|
|pH:||2.0 - 4.0|
|Specific Gravity:||1.00 - 1.05|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
Target dosage range for Accepta 2624 is 150 - 250 ppm as product while maintaining a bacterial count of 103 CFU/mL in the re-circulating cooling water.
Accepta 2624 should be fed neat where it can be uniformly mixed and thoroughly distributed using a chemical metering pump.
Appropriate use of Accepta 2624 following the above dosing strategy should result in a biologically clean cooling system.
It is always advisable to carry out a 'Control Of Substances Hazardous to Health' (COSHH) assessment before use.
For additional assistance please contact Accepta.
- Bacteria count Dip Slides/ATP/Plate Counts
Material of Compatibility
|MS :||Not recommended|
Safety, Storage & Handling
Accepta 2624 is an acidic solution. Avoid contact with skin, eyes or clothing. If skin comes into contact with product, wash with water. If eyes are affected, flush with water for at least 15 minutes and get medical attention.
For full details concerning safety precautions, storage and handling procedures for Accepta 2624 please refer to the latest Safety Data Sheet. To download the latest safety data for this product use the following link: